The Puresine-1000se is designed to focus on AC line correction on both waveform and voltage level. The PS-1000se output is very low distortion Sinewave, less than 0.8% distortion, which is very close to ideal AC line waveform. The equipment connected to PS-1000 will operate at optimum condition resulting in gaining maximum performance. Besides AC line waveform correction, PS-1000se output also stabilizes at 230V+ 0.8% during the AC input fluctuation between 196V - 240V.
1. Venus Engine This advanced design circuit continuously monitors, analyzes and corrects the AC line output waveform and voltage level in analog real-time mode, the AC output is very constant at all time which could not be found in conventional stabilizer in the market.
2. Polaris IV Technology This is Clef proprietary filter technology which is different from common filter design. The common filter design usually filters only high and very high frequency. Polaris filter in PureSINE-1000 is designed to work from 10KHz upward which is the frequency band that affects the sound and video quality. Polaris filter can reduce the noise in AC line over 95% of total noise so the improvement of sound and picture quality can be clearly detected.
3. Vega Filter Technology For video improvement, new Vega filter is used for reduce high frequency noise in video band.
4.Polaris Plus Technology This circuit will remove any DC voltage that may exist on AC line. The equipment will work more efficiently after the DC voltage is removed.
5. Star Wiring Technic This is special technique which totally separate the wiring to each duplex. This will reduce the crosstalk between duplex and increase maximum current delivered the equipment.
Rated input voltage: 196-240 V AC
Spike Protection Modes: L-N, N-G, L-G
Spike Clamping Voltage: 800 V peak @ 3,000 amps, 275 VAC RMS
Response time: 1 nanosecond
Maximum surge current: 13,000 amps (8 x 20 mS pulse)
Maximum spike energy: 1,440 Joules total
Noise attenuation: >10 dB @ 10 kHz, >46 dB @ 100 kHz,
>100 dB @ 1-10 MHZ
Rated output capacity: 1,000 VA (continuous)
Rated output voltage: 230 V AC < 0.8 % or +/- <1.5 V
Rated output current: 5.0 A
Output frequency: 50 Hz
Instantaneous peak current capacity: 15 A
Output waveform THD: 0.2% or less
Input frequency: 50 Hz
No-load power consumption: 45 W
Efficiency: 70 % 1000 W Load @ 240V AC Input
Meter: Dual Digital True RMS Meter
Distortion Input/Output: < 0.2 % @ Input 3%
Dimensions: Width 430 mm (17.0"),
Height 103 mm (4.0"),
Depth 325 mm (12.8”)
Weight: 13.5 Kg net, 14.5 Kg in shipping carton